The factory that uses the air shower sometimes will encounter the air shower room does not blow the phenomenon. When the air shower manufacturer fails to arrive in time to deal with the trouble on the spot, may refer to the following note to check the reason of air shower not blow:
1. First check whether the power supply switch and the emergency stop switch are on, if both reasons are not, check the circuit, whether the leakage switch is closed.How To Choose The Right Air Shower Supplier
2. Whether the IC circuit board is configured to fuse the FUSE safety pipe, and if the fuse fuse is broken, the 4A should be replaced.
3. Check whether the fretting and optoelectronic switches are active, and if not, replace the fretting and optoelectronic switches.Air Purification Methods in Cleanroom
4. If the AC contactor does not work, it will affect the blowing, need to replace the AC contactor.
5. If the circuit board can not output signal to AC contactor coil, it needs to replace IC circuit board.Five Materials Are Used For Transparent Cleanroom Windows Panes
6. No forced opening is allowed when the shower room is blowing. In case of emergency, stop by emergency switch.
|Pharmaceutical Cleanroom Air Shower China Factory|
|Air Shower Nozzle 304 Stainless Steel Adjustable Cleanroom|
|Why Choose Kwang Air Showers|
|What is the classification of clean room?|
|What are the available air shower designs and configurations|